A heavy duty commercial dehumidifier ideal for moving in and out of work vehicles. The rotomoulded case is built tough to withstand knocks. Used in the water damage restoration industry and as a hire machine or where a sturdy, powerful dehumidifier may need to be moved from room to room.
The hot gas defrosting system means the dehumidifier can be used in very cold and/or very hot conditions.
These versatile workhorses can even dry two rooms at the same time. Twin outlets allow two lengths of separate ducting to be run into separate rooms or even into the subfloor.
Well built European pedigree at an affordable price.
- High efficiency
- Hot gas defrosting device with electronic and thermostatic control (optional)
- Fittings for continuous drainage
- Pump for lifting condensed water
- Automatic humidistat
- Hour counter
- Pivoting wheels
- Power supply 220-240V 50Hz
Warranty: 2 years
CONDENSED WATER AT DIFFERENT AMBIENT TEMPERATURE AND HUMIDITY CONDITIONS
|10 l/d||18 l/d||15 l/d||23 l/d||20 l/d||28 l/d||25 l/d||35 l/d||28 l/d||39 l/d||52 l/d||62 l/d|
|Power Consumption (at 27˚C, 65% rh)||700 w|
|Power Consumption (at 35˚C, 95% rh)||950 w|
|Absorbed Current (at 35˚C, 95% rh) standard ver.||4.4 A|
|Start Current Full Load Amp||20 A|
|Air Flow||600 cm/h|
|Noise level (at 3 meters)||53 dB|
|Defrosting Control Standard||Electronic|
|Hot Gas Defrosting Control System||Electronic thermostat|
|Continuous Drainage Pipe (male)||19mm|
|Temperature Range standard version||7-35˚ C|
|Temperature Range (Hot Gas Defrost version)||0.5-35˚C|
|Relative Humidity Range||35-99%|
|Condensation Capacity (at 30˚C, 80% rh)||52 l/24 hr|
|Condensation Capacity (at 32˚C, 90% rh)||62 l/24 hr|
|Dimensions||55cm x 58cm x 93cm|
Product Enquiry:[contact-form-7 404 "Not Found"]
John Holland (I.T. and multi-functional area): Western Australia – FRAL FDSRC 62
Moisture Cure was contacted by a mine site provider and asked to provide a solution. The area was a multi-purpose building of approx. 1200 square metres built to accommodate a variety of work stations. There had been a hold up in the air-conditioning system being installed and commercial dehumidifiers had to be installed to maintain the correct humidity levels.
Moisture Cure recommended the FRAL FDSRC 62 rotomoulded unit complete with condensate lifting pump. Because there were very few drainage points in the building, the collected condensate water was collected in removable plastic bins.
After the completion of the air-conditioning system, these portable commercial dehumidifiers will also be used to complement the air-conditioning system.
John Holland’s comments:
When we found we needed 20 large capacity dehumidifiers quickly we were delighted when Moisture Cure was able to supply this large quantity straight from their stock holdings. In our experience, few companies have this quantity of commercial machines at their disposal.