The FDK 100 is a “no-frills” but robust and reliable dehumidifier capable of extracting large volumes of excess moisture in various commercial situations. Typical uses are medium to large warehouses, commercial agriculture eg: medium to large size greenhouses, Military facilities eg: armouries or storage, museums, art galleries, manufacturing.These machines are also very useful for larger crawl spaces and subfloors.
- Hot gas defrosting device with electronic and thermostatic control
- Non finned tube evaporator
- Four adjustable feet
- Automatic humidistat
- Two strong handles
- Low energy consumption
- Zinc plated and powder-coated sturdy frame
- Can be free-standing or wall-mounted
- Fittings for continuous drainage pipe connection
- Lifting pump (optional)
- Power supply 220-240V 50Hz
Warranty: 2 years
CONDENSED WATER AT DIFFERENT AMBIENT TEMPERATURE AND HUMIDITY CONDITIONS
|20 l/d||34 l/d||26 l/d||42 l/d||34 l/d||50 l/d||44 l/d||62 l/d||52 l/d||62 l/d||90 l/d||110 l/d|
|Power Consumption (at 20˚C, 60% rh)||1200 w|
|Power Consumption (at 35˚C, 95% rh)||1550 w|
|Absorbed Current (at 35˚C, 95% rh) standard ver.||13 A|
|Locked Rotor Current LRA||44|
|Air Flow||1100 cm/h|
|Noise level (at 3 meters)||56 dB|
|Standard Defrosting Control System||Electronic|
|Hot Gas Defrosting Control System (optional)||Electronic thermostat|
|Continuous Drainage Pipe (male)||19mm|
|Temperature Range standard version||7-35˚ C|
|Temperature Range (hot gas defrosting system)||0.5-35˚C|
|Relative Humidity Range||35-99%|
|Condensation Capacity (at 30˚C, 80% rh)||90 l/24 hr|
|Condensation Capacity (at 32˚C, 90% rh)||110 l/24 hr|
|Dimensions||52cm x 52cm x 66cm|
Product Enquiry:[contact-form-7 404 "Not Found"]
Police Station: Yeppoon, Queensland – FRAL FDK 100
Trevor McMasters of McMasters Refrigeration was contracted to find a solution for severe moisture levels throughout the Yeppoon Police Station.
After consultation with McMasters Refrigeration, the contractor, Moisture Cure recommended the FRAL FDK 100. This unit could be modified to be ducted into the air-conditioning ducting.
Moisture Cure was able to evaluate our requirements quickly and make recommendations that we could work with. It was great that these units were in stock and once our decision was made, could be dispatched immediately.
Sponars Chalet Pty Ltd: Mt. Kosciusko, New South Wales – Fral Horizon 100
When Sponars Chalet contacted Moisture Cure they were having trouble with excess condensation in the roof space above their heated pool. Hot, moisture laden air was rising above the pool and entering into the ceiling space above.
This was causing excess moisture in the roofing space, encouraging mould to grow and eventually running down the walls below.
Fral FDK 100 was installed and began removing excess moisture from the pool immediately.